Customer experience dust control issues during and after dosing process.
Customer want to reduce and minimize dust contamination in the dosing room.
Customer have dosing process for warehouse area for Seasoning powder and Spice mixture which generate airborne dust previously without an extraction system for the dosing process, the operator will experience dust cloud during the dosing process.
This result in a dangerous and polluted environment in the dosing room. The contamination is critical as the powder is sticky and cause a high explosion risk environment.
Total 10 station working at the same time which separate to 2 room
2 x DS65600 Dust collector cartridge filter with automatic filter cleaning and control system connect with piping system connected to each room. As the suction media is of sticky nature, we added pre-coating system to prolong the lifespan of the filter.
DS65600 2.2kW Side Channel Blower Drive, 48m2 Cartridge Filter Class M with automatic compressed air filter cleaning mechanism through differential pressure sensor, 20L Automatic Pre-Coating System, Stainless Steel Piping System leading to 6 and 4 Suction Hoods.